Notes from the Field: Mycobacterium abscessus Outbreak Related to Contaminated Water Among Ventilator-Dependent Residents of a Pediatric Facility ― Pennsylvania, 2022
Weekly / October 20, 2023 / 72(42);1151–1152
Jenna N. Sinkevitch, MSPH1,2; Julie Paoline, MA1; Aaron Smee, MPH1; Sophie Jones, PhD3,4; Kevin Spicer, MD, PhD3; Paige Gable, MPH3; Hollis Houston3; Valerie Stevens3; Cara Bicking Kinsey, PhD1 (View author affiliations)View suggested citation
Views equals page views plus PDF downloads
Mycobacterium abscessus, a nontuberculous mycobacterium found in water and soil, is an opportunistic pathogen responsible for waterborne illness outbreaks in health care settings (1). On September 29, 2022, the Pennsylvania Department of Health (PADOH) received notification of M. abscessus–positive respiratory isolates from ventilator-dependent residents of a 34-bed pediatric facility. The facility is licensed for residential services, but not as a health care facility. A case was defined as the first M. abscessus–positive culture identified from a resident of this facility during March–August 2022. Three cases were identified: two colonizations and one clinical infection. PADOH investigated this outbreak to identify risk factors and recommend infection prevention and control (IPC) measures.
On October 12, PADOH conducted a site visit to observe IPC practices. Three instances of respiratory care were observed, during which respiratory therapists failed to follow aseptic technique. Of 37 observed opportunities for hand hygiene, 30 (81%) were compliant. With regard to tracheostomy tube reprocessing (i.e., cleaning and disinfection for reuse), the manufacturer provided different instructions for home care and health care settings; the latter included stricter processes to reduce the risk for pathogen transmission. Staff members did not follow either of the manufacturer’s processes, and instead, created their own procedure using nonmedical cleaning tools and an ultraviolet baby bottle sterilizer for which there is no documentation of effectiveness. PADOH recommended that the facility follow the more stringent manufacturer instructions for tracheostomy tube reprocessing for health care settings* and use aseptic practices during respiratory care. A second site visit on October 31 showed improvement in IPC practices; however, staff members were still not reprocessing tracheostomy tubes following manufacturer recommendations for health care. This activity was reviewed by CDC, deemed not research, and was conducted consistent with applicable federal law and CDC policy.†
Multiple areas of the building had not been in use for 2 years, raising concern about stagnant water and contamination. The facility did not have a water management plan or monitor water quality, as is recommended to prevent water-related infections (2). On October 31, PADOH collected 21 environmental samples from faucets, aerators, showerheads and drains, filtered water and ice machines, and water samples from clinical care areas where residents with M. abscessus colonization or infection resided. Mycobacterium species were identified in 16 (76%) of 21 environmental samples; M. abscessus was identified from a shower drain swab (Table). Heterotrophic plate counts of paired first-catch and post-flush§ water samples in a room sink of a resident and the reprocessing room sink where tracheostomy tubes were reprocessed exceeded Environmental Protection Agency (EPA) standards for safe drinking water¶ (3). PADOH recommended that the facility hire a water management consultant, develop a water management program, and install point-of-use filters in clinical areas until water quality consistently met EPA standards. The facility implemented recommendations in collaboration with a water management consultant; PADOH continued collaborative monitoring for an 8-month period.
Epidemiologic and laboratory evidence suggest that this outbreak of M. abscessus was related to substandard water quality and inadequate IPC practices. Extended disuse of space in the building potentially resulted in stagnant water in plumbing, and the lack of a water management program meant that water quality was unmonitored. The facility licensing requirements did not emphasize IPC standards necessary for residents with high medical needs, including those who are dependent on ventilators. In ventilator-capable congregate settings IPC-recommended procedures should meet health care standards to prevent transmission of infectious organisms.
Corresponding author: Jenna N. Sinkevitch, email@example.com.
1Bureau of Epidemiology, Pennsylvania Department of Health; 2Council of State and Territorial Epidemiologists, Atlanta, Georgia; 3Division of Healthcare Quality Promotion, National Center for Emerging and Zoonotic Infectious Diseases, CDC; 4Epidemic Intelligence Service, CDC.
All authors have completed and submitted the International Committee of Medical Journal Editors form for disclosure of potential conflicts of interest. Hollis Houston reports stock options in Fidelity Healthcare Technology. No other potential conflicts of interest were disclosed.
† 45 C.F.R. part 46, 21 C.F.R. part 56; 42 U.S.C. Sect. 241(d); 5 U.S.C. Sect. 552a; 44 U.S.C. Sect. 3501 et seq.
§ First-catch samples were collected before aerator removal and occurred before the water outlet being sampled was used. Post-flush samples were collected after letting the water run for 5 minutes.
¶ EPA standards for safe drinking water are a heterotrophic plate count ≤500 colony-forming units/mL.
- Lee MR, Sheng WH, Hung CC, Yu CJ, Lee LN, Hsueh PR. Mycobacterium abscessus complex infections in humans. Emerg Infect Dis 2015;21:1638–46. https://doi.org/10.3201/2109.141634 PMID:26295364
- CDC. Developing a water management program to reduce Legionella growth and spread in buildings. Atlanta, GA: US Department of Health and Human Services, CDC; 2021. https://www.cdc.gov/legionella/downloads/toolkit.pdf
- Environmental Protection Agency. 2018 edition of the drinking water standards and health advisories: EPA 822-F-18–001. Washington, DC: US Environmental Protection Agency; 2012. https://www.epa.gov/system/files/documents/2022-01/dwtable2018.pdf
Suggested citation for this article: Sinkevitch JN, Paoline J, Smee A, et al. Notes from the Field: Mycobacterium abscessus Outbreak Related to Contaminated Water Among Ventilator-Dependent Residents of a Pediatric Facility ― Pennsylvania, 2022. MMWR Morb Mortal Wkly Rep 2023;72:1151–1152. DOI: http://dx.doi.org/10.15585/mmwr.mm7242a5.
MMWR and Morbidity and Mortality Weekly Report are service marks of the U.S. Department of Health and Human Services.
Use of trade names and commercial sources is for identification only and does not imply endorsement by the U.S. Department of Health and Human Services.
References to non-CDC sites on the Internet are provided as a service to MMWR readers and do not constitute or imply endorsement of these organizations or their programs by CDC or the U.S. Department of Health and Human Services. CDC is not responsible for the content of pages found at these sites. URL addresses listed in MMWR were current as of the date of publication.
All HTML versions of MMWR articles are generated from final proofs through an automated process. This conversion might result in character translation or format errors in the HTML version. Users are referred to the electronic PDF version (https://www.cdc.gov/mmwr) and/or the original MMWR paper copy for printable versions of official text, figures, and tables.
Questions or messages regarding errors in formatting should be addressed to firstname.lastname@example.org.