Health hazard evaluation report: evaluation of environmental controls at a social assistance facility (Community Rehabilitation Center) associated with a tuberculosis outbreak - Florida.
Martin-SB Jr.; Mead-KR; Lawrence-RB; Beaty-MC
Morgantown, WV: U.S. Department of Health and Human Services, Public Health Service, Centers for Disease Control and Prevention, National Institute for Occupational Safety and Health, HETA 2012-0263-3181, 2013 Jul; :1-28
In May 2012, the National Institute for Occupational Safety and Health (NIOSH) received a request for technical assistance from the Duval County Health Department as part of its response to an ongoing tuberculosis (TB) outbreak among homeless persons in Florida. The request asked NIOSH to assess heating, ventilation, and air-conditioning (HVAC) systems and make recommendations to improve overall environmental controls at four homeless facilities with epidemiologic links to past or ongoing TB disease transmission. During an on-site evaluation of the Community Rehabilitation Center social assistance facility in August 2012, we collected physical and ventilation measurements in all key areas of the facility. We focused on areas where guests typically congregate or spend significant amounts of time. We recorded the make and model number of air-handling units (AHUs) providing supply air to the facility, and visually inspected the units. When possible, we measured the air flow rate through supply diffusers and return grilles. The ventilation systems in place could have contributed to airborne disease transmission among facility guests. With the exception of some window units in the older portion of the main building, the AHUs appeared adequately maintained and were fully operational. Unfortunately, none of the AHUs provided fresh outdoor air to the occupied spaces, as required by the Florida Building Code and American Society of Heating, Refrigerating and Air-Conditioning Engineers design standards. In addition to alleviating odors and maintaining occupant comfort, outdoor air serves to dilute infectious aerosols, such as Mycobacterium tuberculosis droplet nuclei that are responsible for TB transmission. Since the TB outbreak began, Community Rehabilitation Center has taken numerous steps to improve administrative controls, particularly when it comes to identifying guests showing signs and symptoms of TB. We recommend additional improvements to the administrative and environmental controls at the center. From a ventilation standpoint, we suggest that all occupied spaces in the facility are supplied adequate amounts of outdoor air. We also recommend developing a written infection control plan, HVAC operation and maintenance plan, and a written respiratory protection program. Having these plans/programs in place will help the center under normal operating conditions, and especially during future outbreaks of respiratory disease.
Infectious-diseases; Infection-control; Respiratory-system-disorders; Bacteria; Bacterial-disease; Bacterial-infections; Region-4; Ventilation; Ventilation-systems; Heating-equipment; Heating-systems; Air-conditioning-equipment; Air-contamination; Indoor-air-pollution; Indoor-environmental-quality; Disease-transmission; Disease-control; Disease-prevention; Environmental-control-equipment; Environmental-engineering; Environmental-exposure; Engineering-controls; Control-technology; Air-flow; Measurement-equipment; Airborne-particles; Equipment-design; Air-quality; Aerosols; Administration; Humans; Education; Quality-standards; Respiratory-protection; Public-health;
Author Keywords: Vocational Rehabilitation Services; tuberculosis; environmental controls; ventilation; adult education facility; airborne infection; airborne transmission; respiratory
Field Studies; Hazard Evaluation and Technical Assistance
NTIS Accession No.
Healthcare and Social Assistance; Transportation, Warehousing and Utilities
National Institute for Occupational Safety and Health