NIOSHTIC-2 Publications Search
Health hazard evaluation report: HETA-94-0422-2622, Martin County Administration Building, Stuart, Florida.
Martinez-KF; Weber-AM; Trout-DB
Cincinnati, OH: U.S. Department of Health and Human Services, Public Health Service, Centers for Disease Control and Prevention, National Institute for Occupational Safety and Health, HETA 94-0422-2622, 1997 Jan; :1-24
In response to a request, a health hazard evaluation was conducted at the Martin County Administration Building (SIC-9532), Stuart, Florida. One worker had been diagnosed with an immune deficiency, believed to be related to the work environment. The building was a four story structure with approximately 65,000 square feet of floor area. Two roof top single packaged 7.5 ton air conditioning units were placed at the time of construction. In 1987, approximately 50 zoned fan coil units were placed above the suspended ceiling. Bulk samples were collected from the various heating, ventilation and air conditioning systems, which revealed potential fungal reservoirs in certain areas. The air samples collected for culturable fungi and fungal spores did not demonstrate dissemination from these reservoirs. Volatile organic compounds were not identified which could be associated with any of the symptoms the occupants were having, including headache, tiredness, rhinitis, sinus congestion, and respiratory symptoms. Elevated carbon-dioxide (124389) levels suggested that inadequate levels of outdoor air were being introduced into some of the occupied areas of the building. The authors conclude that reported health complaints and symptoms could not be associated with any causative agent present during the survey. The authors recommend that a comprehensive preventive maintenance program be instituted for the air conditioning systems.
NIOSH-Author; NIOSH-Health-Hazard-Evaluation; NIOSH-Technical-Assistance-Report; HETA-94-0422-2622; Hazard-Unconfirmed; Region-4; Air-quality-monitoring; Indoor-air-pollution; Office-workers; Microorganisms; Aerosols; Ventilation-systems; Indoor-environmental-quality
Field Studies; Hazard Evaluation and Technical Assistance
NTIS Accession No.
National Institute for Occupational Safety and Health
Page last reviewed: March 11, 2019
Content source: National Institute for Occupational Safety and Health Education and Information Division