NIOSHTIC-2 Publications Search
Health hazard evaluation report: HETA-95-0362-2587, Jordan Hospital, Plymouth, Massachusetts.
Sylvain DC; Malkin R
Cincinnati, OH: U.S. Department of Health and Human Services, Public Health Service, Centers for Disease Control and Prevention, National Institute for Occupational Safety and Health, HETA 95-0362-2587, 1996 Jul; :1-16
In response to a request from employees at Jordan Hospital (SIC- 8062), Plymouth, Massachusetts an investigation was begun into possible hazardous working conditions. The employees in the Bailey Building reported headache, skin rash, breathing difficulty, hypertension, and fatigue. Specific concern was expressed about exposure to electromagnetic fields produced by a cogenerating facility in the basement of the building. The Hospital was a 130 bed facility with about 400 employees. Walk through inspections and employee interviews were conducted. The authors conclude that no specific single environmental factor was found which would likely be the source of all complaints at the Bailey Building. Some environmental factors which may have been related to some symptoms were found, including humidification using treated boiler steam, the location of building air intakes, and dust and odors from materials used in ongoing construction. The authors recommend that specific measures be taken to improve working conditions, including indoor environmental quality.
NIOSH-Author; NIOSH-Health-Hazard-Evaluation; NIOSH-Technical-Assistance-Report; HETA-95-0362-2587; Hazard-Unconfirmed; Region-1; Ventilation-systems; Indoor-air-pollution; Air-quality-control; Health-care-personnel; Electromagnetic-fields; Indoor-environmental-quality; Author Keywords: general medical and surgical hospitals; cyclohexylamine; extremely-low-frequency electromagnetic fields; indoor environmental quality; treated boiler steam
Field Studies; Hazard Evaluation and Technical Assistance
NTIS Accession No.
National Institute for Occupational Safety and Health
Page last reviewed: September 2, 2020
Content source: National Institute for Occupational Safety and Health Education and Information Division