Health hazard evaluation report: HETA-91-065-2206, Somerset County Assistance Office Building, Somerset, Pennsylvania.
Morgantown, WV: U.S. Department of Health and Human Services, Public Health Service, Centers for Disease Control, National Institute for Occupational Safety and Health, HETA 91-065-2206, 1992 Apr; :1-13
In response to a request from the superintendent of the office, an investigation was made of possible hazardous working conditions at the Somerset County Assistance Office Building (SIC-8399), Somerset, Pennsylvania. Employees had complained of eye and skin irritation and fatigue, particularly during afternoon hours. Temperature and humidity measurements were generally in accordance with recommendations. Mold growth was not found. Levels of airborne contaminants were very low and not expected to cause the symptoms which the workers had reported. The carbon-dioxide (124389) level was such that it would be expected to cause complaints of air quality. When the investigation was conducted, the ventilation system was only partially operative. However, even when the system was in full operation, the measurements indicated that the supply of outdoor air to the building was well below recommended rates for office complexes. The author concludes that the complaints may have been due to substandard ventilation and exposure to cigarette smoke. The author recommends that more outside air be provided to the building and smoking be restricted to certain specified areas of the building.
NIOSH-Author; NIOSH-Health-Hazard-Evaluation; NIOSH-Technical-Assistance-Report; HETA-91-065-2206; Region-3; Hazard-Unconfirmed; Cigarette-smoking; Indoor-air-pollution; Office-workers; Ventilation-systems; Indoor-environmental-quality;
Author Keywords: Social Services, Not Otherwise Classified; indoor air; ventilation; office building; outdoor air supply
Field Studies; Hazard Evaluation and Technical Assistance
NTIS Accession No.
National Institute for Occupational Safety and Health