Health hazard evaluation report: HETA-82-206-1306, New Renaissance Glass Works, Oakland, California.
Cincinnati, OH: U.S. Department of Health and Human Services, Public Health Service, Centers for Disease Control and Prevention, National Institute for Occupational Safety and Health, HETA 82-206-1306, 1983 May; :1-19
An environmental survey was conducted to determine potential exposures to polychlorinated biphenyls (PCB) at the New Renaissance Glass Works (SIC-9999) in Oakland, California on April 2 and 16, 1982. The request for a health hazard evaluation came from the owner after a series of fires and leaks from fluorescent light ballasts. Employees complained of headache, drowsiness, nausea, vomiting, and an acneform rash after the fires. Wipe samples were taken and employees were interviewed. Concentrations of PCB ranged from 31 to 100 nanograms per 100 square centimeters (ng/100cm2). NIOSH suggests an upper background limit of 500ng/100cm2. No airborne concentrations of PCB were detected. Air and cinder block samples were evaluated for lindane (58899), formaldehyde (50000), and chlordane (12789036), but none was detected. The authors conclude that a health hazard exists from PCB from leaking light ballasts. They recommend thorough cleaning to remove dusts containing PCB. Air filter masks should be worn by the employee doing the cleaning.
NIOSH-Author; NIOSH-Health-Hazard-Evaluation; NIOSH-Technical-Assistance-Report; Hazards-Confirmed; Health-protection; Safety-measures; Employee-exposure; Combustion-products; Lighting-systems; Equipment-reliability; Industrial-equipment; Occupational-exposure; HETA-82-206-1306;
Author Keywords: Stained Glass Sales Outlet; fluorescent light ballast; polychlorinated biphenyls; chloracne; press board glue; formaldehyde
58-89-9; 50-00-0; 12789-03-6
Field Studies; Hazard Evaluation and Technical Assistance
NTIS Accession No.
National Institute for Occupational Safety and Health